wireless addressable heat detector is mainly designed for wireless control system. The detector adopts the fastest response and the most sensitive temperature sensing detector. With wireless network alarm function, it can form a wireless local area network alarm system through the panel.Wireless connection, support for electronic coding, easy installation andconstruction.
2.1 Easy to install, mounting bracket included
2.2 High quality durable sensor
2.3 Loud 85dB alarm and LED warning indicator
2.4 Excellent reliability and high stability
2.5 Suitable for all families and other places where needs
2.6 The battery is used for ten years, and it does not need to be replaced for ten years of normal operation.
2.7 Meets all requirements of latest EN standard Technical parameters
3. Technical Parameters
|3VDC (with battery CR17450 / CR17455)
|monitoring status≤8uA, alarm status≤120mA
|433MHz (418MHz to 448MHz)
|Fix temperature Alarm:
|57°C (135°F) A2R
|Rate of rise Alarm：
|Wireless transmit power
|Normal: blinking Alarm: lighting
|Temperature range: 0 to 40°C (32~104°F)
Humidity: ≤93% RH, non-condensing
|Materials and colors
|AW-FP100 addressable fire alarm control panel
|Address from 1 to 250 optional
|105mm* 105mm* 50.2mm (with cover)
4. Mounting base
AW-D604L should comply with all local codes. Shown in Figure 2, install the base of the AW-D604L on the wall. And then insert the main body into the base.
The base dimensions of 105mm*105mm*41mm(Length*Width*Height),mounting hole diameter φ2mm, fixing the hole spacing is 42mm, shown in Figure 3.
Test: When there is no fire alarm, you can press the test button to test. When pressed, both the buzzer and
LED light work intermittently (beep and LED blink)
Mute: when the detector is in the alarm state, press the button on the cover to mute the buzzer, the silence
period for each press is 5 minutes, and the longest does not exceed 15 minutes; if there is still a fire
alarm at the end of each silence period The alarm will be retriggered. Normal work: LED flashes once every 50 seconds and battery power are detected once, smoke density is
detected once every 4 seconds, and the buzzer does not sound. Low battery/failure: LED flashes once every 50 seconds, buzzer beeps once.